The unit sub panel enclosure is setback and has gaps in the drywall greater than the code allowance.
The A/C unit disconnects have inadequate working clearance.
The cables are insufficiently supported as required by code.
The cables within 6 feet of the attic access are not protected from damage.
The recessed lights fixture sockets have been over sprayed with paint/or drywall texture.
The electrical device boxes are setback and have gaps in the drywall greater than code allowances.
The boxes installed in rated walls are improperly installed.
The conduits and/or cables are insufficiently supported as required by code in the electrical closets.
The exterior exposed light fixtures are not sealed to prevent water intrusion.
Quality of Workmanship.